Schedule Services now!
DISCOVERING LONDON, OH
Located about 25 miles southwest of the capital city of Columbus, London was established in 1811. London is a city in Madison County, Ohio with a population of around 10,000. The median age of a London resident is 37 years old.
London grew slowly, having only 297 residents in 1840. This increase was partly due to the completion of two railroads that passed through the town. London is primarily served by the London City School District. Nearby four-year institutions include The Ohio State University, Wright State University, Wittenberg University and The University of Dayton.
London maintains four community parks and public lands that cover 143 acres. The community parks offer facilities for activities including basketball, softball, skateboarding, swimming, and other fitness activities — fun for the whole family!
for London, OH
Dwain - London, OH
the estimator showed up on time and was very thorough with his estimate. The estimate showed up in my email only a couple of hours after his visit.
I completed a job continuation to uninstall furnace for a washer and dryer to be installed and then reinstalled the furnace.
Found furnace locked out, flashing alternating slow, pressure switch trip. Upon departure I found the condensate trap clogged. I blew it out, cycled the power and the system is now heating, Propane furnace 18 years old, recommend regular maintenance and replacement is in its future. Lennox
I completed the scheduled maintenance agreement heating tune up on a Lennox gas furnace. I visually inspected the unit. Checked voltages, amps and pressures. Completed combustion analysis. Cycled and monitored system. Operating normally at this time.
I performed a diagnostic on a Lennox gas furnace and found it flashing code three, which is the pressure switch stuck open or closed. The pressure switch was stuck closed. I broke free and it was heating. It needs replaced. I advised the customer the repair and they approved.
Estimate on a full installation near London Ohio
Trane air conditioning repair