Schedule Services now!
DISCOVERING MARYSVILLE, OH
Marysville is a place where many people say “the Grass is Greener.” Whether that statement is true, or it’s merely a pun used because the city is home to the famous Scotts Miracle-Grow Company, is subject to debate. Perhaps one could say it’s both.
In any case, Marysville is the county seat of Union County, which is 27 miles northwest of Columbus. It has a population of around 25,000 residents and still growing. In December 2008, then First Lady Laura Bush designated Marysville as a “Preserve America Community.”
The community was founded as far back as 1819 by Samuel W. Cuthbertson. Cuthbertson named it after his daughter, Mary. By the late 1820s the town had enough children living there to justify opening its first schoolhouse, which was a log cabin. By 1888, however, the city earned its nickname as “the Shaded City” because of an abundance of maple trees along the town’s streets.
Since 1979, Marysville has been an important location internationally for automotive manufacturing as the community is the home of Honda of America Manufacturing, which makes cars and engines. Although Marysville is large enough to be called a city, people say the city is actually a very rural culture at heart with a wide range of locally-grown food.
for Marysville, OH
I performed a diagnostic on clients air conditioner that was not cooling their home properly. Found capacitor blown. Found filter clean. Cleaned coil. Found system low on refrigerant, added 1/2lb. Suction pressure is 65 liquid is 249. Superheat is 6. Compressor is not pump refrigerant properly and customer is aware. No warranty on refrigerant.
I completed scheduled maintenance agreement on a gas furnace visually inspected the unit cycled and monitored system operating normally at this time
I arrived to do a scheduled maintenance agreement on a American standard gas furnace Technician arrived and completed tune up checklist for safety issues, combustion, and efficiency. Found the furnace was tripping in high limit at 138 degrees when the rating in the hi limit switch is factory set for 180 degrees. Diagnosed bad high limit switch, needs replaced or furnace will be short cycling and shutting off after only a few minutes of running then restart. Customer would like to hold off on the repair at this time
I installed a Five Star 96% 60,000 BTU Gas Furnace 3.5T 17" and a Five Star 15 SEER 3 Ton Heat Pump. I cycled and monitored the systems and they are operational at this time.
Bryant air conditioning repair
Taking care of customer AC issue